To lay down a procedure for generation of the ‘Purified Water’.
This SOP is applicable to Formulations Units.
2.1.1 D.M. Water Plant.
Jr. Technical Officer / Executive - Production
5.2.0 Pre startup
5.4.0 Shut Down
5.1.1 Ensure the water level in the sump.
5.1.2 Before starting the raw water pump make sure that air blower is ‘ON’.
5.1.3 Before starting the degasser pump ensure the water level in degasser tank (should be 1/4th of the tank capacity) as marked on the level indicator.
5.1.4 Before starting the degasser pump ensure that UV lamps are ‘ON’