To lay down a procedure for shut down of Ultra Filtration System.
This SOP is applicable to Formulations Units.
Ultra filtration Room.
Jr. Technical Officer / Executive (Production).
Manager - Production.
5.1 Shut down of the Ultra filtration System to be done in the
5.2 If the microbial count is above 80 cfu/ml.
5.1.2 If any problem arises in pumps (P1,P2,P3)
5.2 Ultra filtration system consist of Ultra filtration unit & closed circulating loop.
5.2.1 Shut down of Ultra Filtration unit.
18.104.22.168 Close the valve V23 and open V24.
22.214.171.124 Stop the pump P1.
126.96.36.199 If the shut down is more than 48 hours following procedure has to be adopted.
188.8.131.52.1 Close the valve V18
184.108.40.206.2 Stop the pump P1
220.127.116.11.3 Close the valve V16
5.2.3 SHUT DOWN OF CLOSED CIRCULATING LOOP
18.104.22.168 Press the push button on the control panel P2/P3 stop.
Note: Users should modify this SOP according to their DQ of the equipment