To lay down a procedure for shut down of Ultra Filtration System.
This SOP is applicable to Formulations Units.
Ultra filtration Room.
Jr. Technical Officer / Executive (Production).
Manager - Production.
5.1 Shut down of the Ultra filtration System to be done in the
5.2 If the microbial count is above 80 cfu/ml.
5.1.2 If any problem arises in pumps (P1,P2,P3)
5.2 Ultra filtration system consist of Ultra filtration unit & closed circulating loop.
5.2.1 Shut down of Ultra Filtration unit.
188.8.131.52 Close the valve V23 and open V24.
184.108.40.206 Stop the pump P1.
220.127.116.11 If the shut down is more than 48 hours following procedure has to be adopted.
18.104.22.168.1 Close the valve V18
22.214.171.124.2 Stop the pump P1
126.96.36.199.3 Close the valve V16
5.2.3 SHUT DOWN OF CLOSED CIRCULATING LOOP
188.8.131.52 Press the push button on the control panel P2/P3 stop.
Note: Users should modify this SOP according to their DQ of the equipment